Vibration issues with a two-stage pump forced a major steel manufacturer to remove the pump from service. Due to incorrect weights welded on an impeller, a steel manufacturer called upon Hydro to repair and balance a two-stage pump.
Written by: Ken Babusiak (Hydro, Inc.)
Published by: World Pumps
The pump was experiencing the vibration during the spring and summer months of 2016. The steel company sent the pump to HydroAire’s Chicago, IL facility in September of that year. HydroAire was able to determine the cause of the vibration and created a solution that got the pump back in operating condition. The pump was installed and back in service by February, 2017.
The initial testing and analysis deter-mined that the impeller had large weights welded onto it. The steel company was concerned for many reasons, especially because the staﬀ knew that using weights was not the correct way to balance an impeller. This caused the steel manufacturer to question the manner in which the pump had previously been repaired.